To establish minimum indoor air quality (IAQ) performance to enhance indoor air quality in buildings, thus contributing to the comfort and well-being of the occupants.
Case 1. Mechanically ventilated spaces
Option 1. ASHRAE standard 62.1-2007 or non-U.S. equivalent
Mechanical ventilation systems must perform according to the ventilation rate procedure.
Modify or maintain existing building outside-air ventilation distribution system to supply at least the outdoor air ventilation rate required by ASHRAE Standard 62.1-2007 (with errata but without addenda1). Projects outside the U.S. may use a local equivalent to ASHRAE Standard 62.1-2007 for breathing zone minimum ventilation rates.
Option 2. CEN standard EN 15251: 2007
Projects outside the U.S. may modify or maintain each outside air intake, supply air fan and/or ventilation distribution system to supply at least the outdoor air ventilation rate required by Annex B of Comité Européen de Normalisation (CEN) Standard EN 15251: 2007, Indoor environmental input parameters for design and assessment of energy performance of buildings addressing indoor air quality, thermal environment, lighting and acoustics.
If the project team cannot meet the outside air requirements of the above standards, document the space and system constraints that make it not possible, complete an engineering assessment of the system’s maximum cubic feet per minute (cfm) capability toward meeting the requirements of the above standards, and achieve those levels, with a minimum of 10 cfm (0.28 cubic meters per minute) per person. All other requirements must be met.
Case 2. Naturally ventilated spaces
Naturally ventilated buildings must comply with ASHRAE Standard 62.1-2007, Paragraph 5.1 (with errata but without addenda1). [Europe ACP: Arbeitsstaettenrichtlinie ASR 5]
Alternative Compliance Paths (ACPs)
Europe ACP: Arbeitsstaettenrichtlinie ASR 5
Projects in Europe may use Arbeitsstaettenrichtlinie ASR 5 as a local equivalent to ASHRAE Standard 62.1-2007, paragraph 5.1.
Credit substitution available
You may use the LEED v4 version of this credit on v2009 projects. For more information check out this article.
Ask questions, share tips, and get notified of new forum posts by joining LEEDuser, a tool developed by BuildingGreen and supported by USGBC!