To conserve water used for cooling tower makeup while controlling microbes, corrosion, and scale in the condenser water system.
For cooling towers and evaporative condensers, conduct a potable water analysis within five years of submission for certification, measuring at least the five control parameters listed in Table 1.
Table 1. Maximum concentrations for parameters in condenser water
|Ca (as CaCO3)||1000 ppm|
|Total alkalinity||1000 ppm|
ppm = parts per million
µS/cm = micro siemens per centimeter
Calculate the number of cooling tower cycles by dividing the maximum allowed concentration level of each parameter by the actual concentration level of each parameter found in the potable makeup water. Limit cooling tower cycles to avoid exceeding maximum values for any of these parameters.
Table 2. Points for cooling tower cycles
|Cooling tower cycles||Points (except data centers)||Points (data centers)|
|Maximum number of cycles achieved without exceeding any filtration levels or affecting operation of condenser water system (up to maximum of 10 cycles)||2||2|
|Achieve a minimum 10 cycles by increasing the level of treatment in condenser or make-up water
OR Achieve the number of cycles for 1 point and use a minimum 20% recycled nonpotable water
Ask questions, share tips, and get notified of new forum posts by joining LEEDuser, a tool developed by BuildingGreen and supported by USGBC!