Reduce bird injury and mortality from in-flight collisions with buildings.
Comply with the Facade Monitoring Plan requirements, one of the Interior Lighting options, and one of the Exterior Lighting options below.
Façade monitoring plan requirements
Develop a three-year building facade monitoring plan to routinely monitor the effectiveness of the building design in preventing bird collisions. Include methods to identify and document locations of the building where repeated bird strikes occur, the number of collisions, the date, the approximate time (if known), and features that may be contributing to collisions. The plan should also provide a process for corrective action. Use the monitoring plan as the baseline for the measures implemented during the performance period.
Interior Lighting Requirements
Develop a lighting design strategy to effectively eliminate or reduce light trespass from the building. The lighting in all spaces with a direct line of sight to exterior fenestration shall meet at least one of these two options:
Option 1. nighttime personnel
Include a requirement in any building operations guidelines stating that all interior lighting must be turned off by the appropriate nighttime personnel after hours when the space is unoccupied, or at a minimum from midnight until 6 a.m.
Option 2. automatic shutoff
The lighting shall be controlled such that all lighting in the space will be automatically shut off after being vacant for a period of no longer than 30 minutes.
Exterior lighting requirements
Develop a lighting design strategy to effectively reduce or eliminate light trespass from exterior fixtures. Meet the exterior and garage lighting power density and controls requirements in sections 126.96.36.199, 188.8.131.52, 9.4.3, of the ANSI/ASHRAE/IES Standard 90.1- 2010 (with errata but without addenda).
Option 1. fixture shielding and automatic shutoff
Shield all exterior fixtures such that the installed fixture does not directly emit any light at a vertical angle more than 90 degrees from straight down. Exterior building fixtures that are not necessary for safety, building entrances, and circulation shall be automatically shut off from midnight until 6 a.m.
Option 2. new construction SS credit, light pollution reduction
Demonstrate that the project complies with the exterior lighting requirements of the latest published LEED for New Construction SS Credit, Light Pollution Reduction.
Implement the façade monitoring plan for a period of three years. If results of the monitoring plan indicate that areas of the building receive multiple collisions, consider implementing temporary and/or permanent retrofits to the building façade.
General Pilot Documentation Requirements
- Participate in the LEEDuser pilot credit forum
- Complete the feedback survey:
- If all materials on the building have a Threat Factor of 15 or below and the project did not perform the calculations, submit a narrative describing why the materials, and building in general, are “bird-friendly.” This includes a material list and supporting data.
- A completed Bird Collision Threat Rating spreadsheet.
- Plan(s) and/or elevation(s) depicting the location of all materials and shading/screening devices used to comply with this credit
- Applicable specification details on all materials and shading/screening devices used to comply with this credit
- A copy of the building operations guidelines text that stipulates that all interior lighting must be turned off by the appropriate nighttime personnel after hours when the space is unoccupied.
- Narrative, and drawings showing control locations, describing the lighting controls used on the interior lighting, the sequence of operation and how these controls comply with this credit and section 9 of the ANSI/ASHRAE/IES Standard 90.1-2010
- A photometric report of those luminaires demonstrating that no light is emitted above 90 degrees from straight down in their final installed position(s).
- Narrative, and drawings showing control locations, describing the lighting controls used on the exterior lighting, the sequence of operation and how these controls comply with this credit.
- All submittals required for the LEED for New Construction SS Credit, Light Pollution Reduction.
Post-Construction Monitoring Plan
- A copy of the post-construction monitoring plan
- Provide records of all collisions during the Performance Period. Include the location, date, and approximate time of day for each collision.
- Plan(s) and/or elevation(s) depicting the location of all temporary and permanent materials and shading/screening devices used to retrofit the building façade in response to the results of the monitoring plan.
- Applicable specification details on all temporary and permanent materials and shading/screening devices used to retrofit the building façade in response to the results of the monitoring plan.
Ask questions, share tips, and get notified of new forum posts by joining LEEDuser, a tool developed by BuildingGreen and supported by USGBC!
No sample form available for this credit.View all sample forms