To begin the commissioning process early in the design process and execute additional activities after systems performance verification is completed.
Implement, or have a contract in place to implement, the following additional commissioning process activities in addition to the requirements of EA Prerequisite 1: Fundamental Commissioning of Building Energy Systems and in accordance with the LEED Green Building Design and Construction Reference Guide, 2009 Edition Healthcare Supplement:
Option 1 (1 point)
- Prior to the start of the construction documents phase, designate an independent commissioning authority (CxA) to lead, review and oversee the completion of all commissioning process activities. The CxA shall, at a minimum, perform Tasks 2, 3, and 6. Other team members may perform Tasks 4 and 5.
- The CxA must have documented commissioning authority experience in at least two building projects.
- The individual serving as the CxA:
- Must be independent of the work of design and construction.
- Must not be an employee of the design firm, though he or she may be contracted through them.
- Must not be an employee of, or contracted through, a contractor or construction manager holding construction contracts.
- May be a qualified employee or consultant of the owner.
Option 2 (2 points)
Achieve OPTION 1 AND
Commission the building’s thermal envelope systems in accordance with the requirements of Option 1. Commissioning of the building envelope shall be in accordance with ASHRAE Guideline 0-2005, the Commissioning Process, and National Institute of Building Sciences (NIBS) Guideline 3-2006, Exterior Enclosure Technical Requirements for the Commissioning Process.
The building thermal envelope entails all exterior wall assemblies separating a building’s conditioned spaces from outdoor ambient conditions, including: roof assemblies, vapor barriers, diffusion retarders, air barrier systems, rain-screen layers, flashings, cladding and siding, windows, curtain-wall assemblies, doors, thermal bridges , and utility penetrations, such as piping, electrical conduit, duct-banks and other entry-points made for routing HVAC system components. For major renovations, substantial performance upgrades must be installed on at least 25% of the exterior envelope surface area.
In support of the process requirements in Option 1, the following sequence of steps shall be taken to ensure an effective building thermal envelope commissioning process:
- Convene meeting to review with the entire green building project team the goals and objectives of the process and coordinate/assign the related tasks.
- Conduct building thermal envelope design review.
- Develop thermal envelope commissioning work plan and schedule.
- Develop coordinated documentation plan.
- Ascertain functional performance test and inspection procedures (i.e. determine reference standards).
- Review thermal envelope components and assemblies mock-ups where relevant.
- Conduct scheduled field quality assurance inspections per work plan; document inspections.
- Inspect corrections of defects encountered during inspections.
- Prepare final report.
Note: These are typical steps, but not the only options available.
Ask questions, share tips, and get notified of new forum posts by joining LEEDuser, a tool developed by BuildingGreen and supported by USGBC!