Achieve increasing levels of energy performance above the prerequisite standard to reduce environmental impacts associated with excessive energy use.
Reduce design energy cost compared to the energy cost budget for energy systems regulated by ASHRAE/IESNA Standard 90.1-1999 (without amendments), as demonstrated by a whole building simulation using the Energy Cost Budget Method described in Section 11 of the Standard.
[INSERT TABLE HERE]
Regulated energy systems include HVAC (heating, cooling, fans and pumps), service hot water and interior lighting. Non-regulated systems include plug loads, exterior lighting, garage ventilation and elevators (vertical transportation). Two methods may be used to separate energy consumption for regulated systems. The energy consumption for each fuel may be prorated according to the fraction of energy used by regulated and non-regulated energy. Alternatively, separate meters (accounting) may be created in the energy simulation program for regulated and non-regulated energy uses.
If an analysis has been made comparing the proposed design to local energy standards and a defensible equivalency (at minimum) to ASHRAE/IESNA Standard 90.1-1999 has been established, then the comparison against the local code may be used in lieu of the ASHRAE Standard.
Project teams are encouraged to apply for innovation credits if the energy consumption of non-regulated systems is also reduced.