ID#2045 made on
EQc5 - Indoor chemical and pollutant source control
LEED BD+C: New Construction, LEED BD+C: Core and Shell, LEED BD+C: Schools, LEED ID+C: Commercial Interiors, LEED O+M: Existing Buildings
Rating System Version:
v3 - LEED 2008, v2 - Schools 2007, v2 - LEED 2.2, v2 - LEED 2.0
Our question regards the filtration requirement for re-circulating air systems, such as VAV terminals and fan coil units, under EQc5. Per LI 5061 and LI 1795 rulings, "Since the fan coil units re...
**Updated January 1, 2014
As noted in LI 5061 and LI 1795 rulings, both outside air and re-circulated air must pass through MERV-13 filtration before being introduced into a space, even if the re...